How to Replace a Hot Water Heater
Replacing a Hot Water Heater
Replacing an electric hot water heater is a simple task that most homeowners can easily perform. The addition of gas piping and vents can complicate the matter slightly, but even that is not so difficult for the do-it-yourself type of person.
- As always in performing such a task, the first step is removing all sources of supply and/or energy to the hot water tank. Turn off the water, either at the main valve feeding the house or at the hot water heater. Most heaters will have a valve on the cold water coming into the heater, and it is sufficient to turn off that valve. Turn off the power to the heater at the panel board. Turn off the gas supply. Safety cannot be emphasized enough; electric water heaters will normally be supplied with a dangerous 240 volts and you certainly don't want gas flooding the house! Make sure that circuit breakers, fuses, water, and gas valves are all turned off.
- Be aware of the time involved. If the main water valve to the home is turned off, the home will have no water for a couple of hours or even more if plumbing needs to be redone. Make appropriate arrangements for at least a limited amount of water during that period.
- Remove the old water heater (see instructions below).
- Install the new unit (see instructions below).
Removal of the Old Water Heater
- Carefully remove any insulation from around the hot water heater. If possible, save this insulation for later reuse, but if it is torn and ruined, you will need to purchase and install new insulation.
- Drain the tank. There should be a valve at the bottom of the tank that will accept a water hose; attach a garden hose, run the other end outside, and open the drain valve. Be aware that there will probably be rusty water coming out; don't position the hose in a place where it will stain a nice patio or other surface.
- Open both hot and cold water valves somewhere in the house. (Maintenance tip to extend the life of your unit: once a year, it's a good idea to partially drain the water heater in this fashion to remove the inevitable sediment build-up in the bottom of the tank.)
For electric water heaters: On the top, there will be a small steel plate where the wiring enters the tank. Remove the plate and gently pull the wires out. Using a non-contact voltage tester (if you don't have one, this is a good time to buy one), test the wires for the presence of voltage. As noted, since it will most likely be 240 volts, contact will result in injury or death, so make sure the circuit is off and there is no voltage present! Disconnect all wires from the old
For gas water heaters: Remove the connections to any gas piping and test the pipe for gas leaking through the previously-closed valve. It is a good idea to cover the exposed open gas pipe with a cloth or tape to prevent any debris from falling in.
- Using a pipe wrench or adjustable wrench (depending on the type of connection), remove the water piping from the top of the water tank. There may be a small amount of water lost from the piping as it is removed, so be prepared with a towel or rag to mop up small spills. If there is more than a cupful of water coming out, the water is not turned off.
- Carefully bend the flexible water pipe up and out of the way just enough to remove the water tank. Inspect this flexible piping carefully: if it needs replacement, now is the time to do it, and these short pieces are not expensive. If in doubt, replace them.
- Using help if needed (water tanks are fairly heavy and quite bulky and awkward), remove the water heater and set aside for disposal.
Installation of the New Hot Water Heater
- Position the new hot water tank into the space where it will rest, and turn it to the proper orientation. Hopefully water, electric, and gas piping outlets will be at least near the same locations, but remember that the cover plates on the side of the tank cover the heating elements, and these elements need to be accessible for future maintenance. If at all possible, arrange the tank so that the cover plates can be reached.
- Wrap any threaded (male) pipe fittings with two or three layers of teflon plumbers tape and re-install the water pipes. When applying the tape, start at about 1" from the end of the fitting and wrap the tape in a clockwise manner around the pipe, overlapping at least 1/2 with each rotation. The entire threaded area of the pipe should be covered with two layers of tape. If the tape is wrapped the wrong direction, the action of screwing the pipe in will tend to dislodge it. If this happens, simply remove the tape and re-wrap in the other direction.
- Pipes should be tightened firmly with a wrench, but do not over-tighten copper threads. Loose and leaking joints can be tightened, but piping damaged from tightening too far will need replacement.
- Turn on the water and check for leakage at all joints. Wipe all joints dry and check after several minutes for any leaks. Even a drop of water per minute is unacceptable.
For a gas unit: Re-connect any gas piping, open the gas valve, and check for gas leakage by putting soapy water over all pipe joints. Any bubbles at all indicate leakage that must be corrected; there must be absolutely no gas leakage at all.
For an electric unit: The plate removed from the old water heater will have to be removed from the flexible conduit it is attached to; there is a large nut on its bottom for that purpose. The ground wire will also need to be removed, but pay attention to where it goes and how it is attached, as the new water tank will have a very similar, but probably not identical, setup. Attach the new plate to the flex conduit and re-attach the ground (green or bare) wire. Using new wire nuts, attach the other two incoming wires to the two in the hot water tank. With a 240 volt supply, it won't matter which wire goes to which (except for the green or bare ground wire), but small apartment tanks may operate on 120 volts and the white supply wire must attach to the white heater wire with the two black wires connecting to each other.
- Fill the tank by opening a hot water tap in the house and waiting until water comes out.
- Turn on the circuit breaker or fuse or light any pilot lights according to the new heater's instructions.
- It is a good idea to keep an eye on the water piping for a few days for any leaks. Hot water and pressure could cause otherwise tight joints to leak slightly and they could need tightening.
- Reinstall the insulating blanket. If the old water heater did not have insulation, it is strongly recommended that it be purchased and installed. The insulation blanket is one the easiest and cheapest ways to save energy in your home.
Congratulations! You have installed your own water heater, and it didn't cost an arm and a leg for a plumber to come and perform this simple task.
Questions & Answers
© 2010 Dan Harmon