Cold Water Header Tank Overflowing: How to Replace a Ballcock Washer
Leaking Valves, Overflowing Water Tanks and Toilet Cisterns
You hear water running outside your home. You look up and see a pipe sticking out from the edge of the roof or soffit which you've never even noticed before. Water is trickling out from the pipe and down onto the ground.
That mysterious pipe is the overflow from the cold water header tank (also called a cistern) in your attic. If the tank overfills, excess water flows safely via the overflow to the outdoors. It's not likely to be a catastrophe, and the flow may only be a trickle, but if you have a water meter and pay for your water, obviously the cost of this wastage can add up.
This guide explains the basics of the pipes and valves in home plumbing systems and how to remedy an overflowing cold-water tank in the loft. This tank is commonly found in UK plumbing systems. You can use the same repair principles for remedying a leaking toilet cistern. There is some variation in the type of valves fitted to tanks. Newer tanks are fitted with diaphragm valves, whereas older tanks use a sliding valve system with a replaceable washer as shown in the photos below.
Note: This article covers replacing a washer in an old style ballcock valve (part 1 valve). This valve is actually against regulations in new installations. There are several different types of valves different to the one below, but all of them use some form of fiber/rubber washer/O-ring/diaphragm system to shut off flow.
What Is the Cold Water Tank in the Attic For?
The cold tank in the loft serves three purposes:
- It collects expanding water as it rises in the expansion tube when the water in the hot tank is heated. Nowadays, an expansion vessel may be used in some systems to accommodate water as it expands when heated.
- The second function of the tank is to provide a pressure head and feed for the hot water tank (gravity feed). Water flows out from the bottom of the cold tank (the blue line in the diagram below) to the bottom of the hot tank. Because the cold tank is higher than the hot tank, the resulting pressure forces water through the tank and out the top. Water in the hot tank is heated by an electric (immersion) element and/or heating system boiler (furnace). Modern hot water systems use a pump to provide the pressure.
- It acts as a storage reservoir and can supply water in the event of an interruption in supply from your water company. This cold water supplies WCs, showers, baths and hand basin taps (faucets). The water isn't drinkable and shouldn't supply the cold taps in the kitchen because it has been lying indefinitely in an open tank into which anything could have dropped (insects, spiders, and possibly birds, bats and their droppings!).
Older buildings only use the tank in the attic for pressurizing the hot water tank and water is fed from the rising main to all fixtures. This is called a "direct system". In some countries, the tank isn't common and pressure for the hot water supply is derived from the incoming mains or a pump.
Indirect and Direct Plumbing Systems
- Indirect Plumbing system. The cistern/tank in the loft and also the cold tap in the kitchen is fed by the rising main. All other cold taps and water fittings get their supply from it. The cistern also creates the pressure for the hot water tank
- Direct plumbing system. All cold taps are fed from the rising main. This is less complicated, but the high water pressure can cause noise and water hammer in taps.
Domestic Plumbing Systems: Pipe Layout in House (Indirect Plumbing System)
The diagram below outlines the most basic plumbing arrangement in a house. This is an indirect plumbing system which is found in most homes.You may have extra plumbing fixtures, but the basic principle is the same, although the hot water tank can be located on the ground floor or on upper floors. Some older houses may not have a tank in the loft.
Inside the house, several gate or ball valves allow water to be shut off to various sections of the plumbing system. A gate valve has a wheel/knob which is turned clockwise to shut off flow. A ball or quadrant valve has a lever handle which is lined up with the pipe when the valve is on. To turn it off, the handle must be turned through 90 degrees so that it is perpendicular to the pipe. There may also be small, inline isolating valves for disconnecting water to each appliance. These are operated with a slotted head screwdriver.
How Valves Are Used to Isolate Sections of the Plumbing
Water enters the building at ground level.
- Valve 1 is located directly outside the premises on a wall or in a box in the ground. This normally has a square section on the end of the shaft and needs to be operated with a key. In colder climates, it may be in the basement. This enables the water supply entering the building to be cut off. Unlike a gate valve, this valve has a rubber seal which tightens against a seat so that water can be totally shut off. There may be another stopcock outside the boundary of the premises under an inspection cover but sometimes this is shared and cuts off water to several homes
- Valve 2 located indoors is the main stop cock, and shuts off water where the service main enters the building. Drinking water must not be supplied from the tank in the loft, and comes directly from the service main.
- Valve 3 shuts off the feed to the cold water tank in the loft to allow maintenance or drainage of the tank.
- Valve 4 shuts off the cold feed to the bottom of the hot tank, removing the pressure, and this prevents hot water leaving the top of the tank.
- Valve 5 shuts off feed to WCs, baths, showers, wash basins etc. There may only be one feed pipe from the cold tank to both the hot water tank and these fixtures, in which case there will only be one valve to shut off this supply, i.e one valve shuts off both cold water and hot water (because pressure is removed).
You may have additional valves feeding each appliance. These valves are usually small isolating types which are operated by turning a screw or short lever.
The hot tank is vented to the atmosphere via an expansion pipe which runs up into the loft to the cold tank. This allows expansion to take place without restriction as water is heated. Also if the heating system malfunctions and water in the tank boils, steam can escape and water can flow safely back into the cold tank.
Indirect Plumbing System
What Is the Small Tank in the Loft for?
If you have an open or vented heating system, there will also be a small reservoir tank in your attic. This is a top-up reservoir for water in radiators and boiler, and also collects water as it expands in the heating system. An expansion pipe runs from the boiler up to the tank and then bends downwards over the tank so that water can drain. If your central heating system overheats, this pipe can also vent steam. Overheating could be caused by faulty thermostats forcing an oil or gas boiler to remain on all the time, but more likely due to a circulating pump failure (or loss of power to the pump) on a solid fuel system with a back boiler and the radiators upstairs turned off.
Alternatively, a failed immersion thermostat could cause water to boil in the tank. The tank is normally fed by the same cold water pipe as the larger tank. This small tank also has a ball cock which can suffer from the same problems as the main cold water tank.
How Does a Ballcock Valve Work?
The tank in the loft is fitted with a ballcock valve (also known as a balltap or float valve) to prevent it over filling. This is the same as the system used in a toilet cistern. Water enters via the valve, and as the level in the tank rises, it pushes upwards on the underside of a plastic or brass float attached to a lever arm. The leverage of the arm creates sufficient force to close the valve once the tank has sufficiently filled.
What Causes the Cold Tank to Overflow?
- The float has developed a leak so that it fills with water, sinking, or providing insufficient force to close the valve
- The rubber washer in the valve has deteriorated so that it doesn't seal properly
- The brass nipple in the valve has worn to such an extent from decades of abrasion by particles in the water that it won't seal anymore. (a ridge can develop in the wall of the nipple's tip. In this case, the valve will have to be replaced
Any of these scenarios will cause the water level to rise in the tank, eventually causing an overflow.
What Tools are Needed to Replace a Washer in the Ballcock Valve?
- or alternatively a Water pump pliers or vise grips pipe wrench (Stilson wrench)
- Flat blade screwdriver
- Small pliers
- Long-nose (snipe-nose) pliers (not essential, but useful for pulling out the split pin)
- Torch (ideally a head torch)
These are just some of the 20 Essential Tools You Need For Home Maintenance
Step 1: Turn Off the Valve on the Pipe Feeding the Tank
As described in the explanation of plumbing systems above, this is valve 3. This may be located downstairs, near the cold tank or near the hot tank. You will have to trace the piping and by a process of elimination, identify which valve controls what. If you push the float of the ball cock downwards and no water flows into the tank, you have found the right valve. Usually valve 3 (shown in the diagram above) feeding the tank is on a 1/2 inch / 15 mm pipe.
Step 2: Remove the End Cap From the Valve in the Tank
The valve on this tank is a slider type. Inside the body of the valve is a nylon or brass slider with a rubber washer embedded in the end. Water flows out through a nipple inside the valve. The slider is pushed against this nipple by the float arm and this cuts off flow.
Using the water pump pliers, pipe wrench or vise grips, unscrew the end cap. If it's obstinate and refuses to turn, try pouring some hot water from a kettle over the cap, this should expand it slightly and make it easier to turn.
Step 3: Remove the Split Pin
A split (cotter) pin holds the float arm in place. Squeeze the two ends together with the pliers. Now use the long nose pliers to grip the looped end of the pin and pull it out. If you rotate the pin backwards and forwards while pulling, it makes it easier. If it's really tight, tap it with a hammer (don't hit it hard, just use lots of light taps).
Step 4: Remove the Float Arm
There is a knack to doing this. Move the float arm into a horizontal position and then pull it downwards. You will likely need to wiggle it a bit to get it out.
Step 5: Check the Float
Over time, floats can become cracked or develop leaks where they screw onto the arm. Shake the float to see whether there's any water in it. You can buy replacement floats in a hardware store.
Step 6: Remove the Slider
Push a narrow blade screwdriver up into the slot in the underside of the valve. Push the slider so that it sticks out of the valve body. You won't get it all the way out with the screwdriver, so grip the end and pull it out with your fingers or nails.
If the washer looks ok and isn't excessively worn, the nipple in the valve might be worn so that it doesn't seal properly against the washer. If this is the case, consider replacing the complete valve. A new valve will have a push type fitting suitable for connecting to copper or plastic tubing, or alternatively a compression fitting. You can read more about these type of fittings in A Complete Guide to Using Plumbing Fittings for Joining PVC, PEX, and Copper Pipe.
Step 7: Remove the Washer
Push it out with a screwdriver.
Step 8: Replace the Washer
You can buy a washer in a store or make one from a suitably thick scrap of sheet rubber. If you are making one, use the perimeter of the slider as a guide and then pare to fit. Push the washer back into the slot of the slider, using the screwdriver to stop the rubber catching in the edges of the slot. Once you get it in halfway, lay the valve on its side and push it in fully with your thumbs.
Step 9: Replace the Slider, Float Arm and End Cap
Push the slider back into the valve body ensuring that the slot in the slider is aligned with the slot in the underside of the valve body. You can use the screwdriver to feel whether it is lined up. Replacing the float arm can be tricky if the two slots don't line up. Hold the arm horizontally and push upwards, wiggling it a bit helps to get it into place. Push the split pin back into place and splay the two ends slightly apart with a screwdriver. They don't need to be spread far apart. Replace the end cap and screw tight, hand tight is good enough. A smear of Vaseline on the threads helps to prevent seizing should it be necessary to remove the cap in the future. You can do this on threads of taps also when re-assembling.
Step 10: Turn the Water Back On
Turn the water back on. Hold the underside of the lever arm, and pull it upwards to validate that the valve cuts off water properly. Initially water will gush into the tank and the level will rise quickly. However as the tank fills, the valve will start to close and flow will dwindle, so it can take ages for water to stop dripping because of the slow rise of water level. Don't worry if this is the case.
Adjusting Ballcock to Change Water Level
In a toilet cistern, you can conserve water by placing a plastic bottle filled with water into the tank. This reduces the amount of water used every time you flush. Alternatively, you can use a piece of brick or other heavy object. Another option is to adjust the ballcock arm so that it shuts off the water valve when the water level is lower.
If there is no screw which facilitates making an adjustment and the arm is the older-style brass type, hold the arm securely in the middle so as not to damage the valve. With your other hand, grasp the arm just before the ball float. Bend the arm downwards so that it ends up being curved downwards. Water will now force the float to act on the arm and close the valve at a lower level. Newer style ballcock valves have a screw for adjusting level. Turn the screw clockwise to reduce the level to which the tank fills.
How to Stop a Cold Tank From Freezing in Winter
Modern lofts have their floor insulated so not a lot of heat permeates up into the loft space, especially if upstairs radiators are turned off. The result is that the cold water tank can start to freeze. If you're regularly running taps and using the shower, the main cold tank continually fills with new water, so this is less likely to happen, but pipes in the attic can freeze and burst if a home is vacant for a couple of days during extended snowy and cold periods. This is especially the case if plumbing is copper, and pipes can freeze in very cold weather even if they're lagged. PEX plumbing because it's flexible, is better at tolerating sub-zero temperatures because the plastic has more "give" and can stretch.
The smaller water tank used for topping up the central heating system and collecting water as it heats up and expands (or the system overheats and water boils) is much more likely to freeze because water isn't continually replaced. So in cold weather, it's a good idea to leave the trapdoor to your attic open and allow some heat up into the space to prevent this happening.
Be Prepared! Plumbing Tip
The Boy Scout motto is "Be Prepared!" so take a leaf out of their book by locating and identifying all the valves in your home! Work out what they do and write the function on the wall behind with a thick marker. Alternatively, tie a label around the stem of the valve. Gate valves can seize up after years of disuse so every so often (once a year), give them some exercise by turning on and back off again. If a pipe springs a leak in your home, you don't want to be running around figuring out how to turn off the water.
This article is accurate and true to the best of the author’s knowledge. Content is for informational or entertainment purposes only and does not substitute for personal counsel or professional advice in business, financial, legal, or technical matters.
Questions & Answers
Why is the overflow still dripping after replacing the ballcock?
Presumably this is because water is rising too high and reaching the level of the overflow outlet. If the overflow pipe still drips after replacing the ballcock, check first that the ball on the end of the lever can move unrestricted in the tank and there isn't anything obstructing it. If you didn't replace the ball float, this could be punctured, slowly letting in water and partially full. The result is that water would need to rise higher to create sufficient force to close the valve. Another possibility is that adjustment is necessary because the new ballcock has a different length arm. If it has an adjustment screw, turn this anti-clockwise or clockwise so that the valve shuts off when the water has reached a lower level.Helpful 50
I have no hot water. What could be the problem?
If you have a cold water tank in the loft, this produces the pressure to force water out of the hot tank. A valve, sometimes located in the hot press, turns on the cold water feed to the bottom of the hot tank which forces hot water out the top. This may be a quadrant valve which has a lever. The lever should be parallel to the pipe and perpendicular to the pipe when off. It is possible for the valve to be inadvertently knocked off, so just turn it back on. Before you do this, however, you need to confirm that it is not a gas valve which has been turned off for some reason.
Why does the overflow from my header tank drip during the night but not during the day?
During the day, you're using water regularly, so the water level never reaches the overflow outlet. At night the water level may be slowly rising due to a trickle of water flowing into the tank from a faulty ballcock valve, so it has plenty of time to reach the overflow.Helpful 17
I have two header tanks up in my loft, one big tank and another small tank with a similar configuration. Why is tank number two overflowing to the roof?
The smaller tank is likely to be the expansion tank for the central heating system. Just like the main cold water tank, this will overflow if the ballcock washer is worn or if it is set up so that water level reaches the overflow before the float shuts off the valve.Helpful 3
I've replaced completely the 3/4" ballcock on my loft water storage tank serving my power shower. However the I'm having difficulty aligning the threaded female elbow connection to the existing pipework. How do I achieve a watertight seal when the elbow isn't fully tightening on the ballcock inlet? I have fully tightened the elbow is 90 degrees out of the previous position.
I'm not a plumber, so I don't know whether this is the recommended solution, but I had a similar problem attaching an elbow to the ballcock in a toilet cistern. I simply use more PTFE sealing tape so that the fitting starts to tighten up a couple of threads before the male part reaches the "end of the line" on the threads in the female elbow. If you discover that you've gone too far, and the fitting can't be tightened further around to the correctly aligned position, don't loosen it, to re-align as it may leak. Undo and re-apply tape again. It might be helpful to post on plumbing forums to get a second opinion.Helpful 2
© 2014 Eugene Brennan