How To Replace A Fluorescent Ballast
Replacing A Ballast
Replacing a fluorescent ballast is not a terribly difficult job; as a professional electrician I have replaced hundreds of ballasts and it normally takes about 10 or 15 minutes if the light fixture itself isn't something special and difficult to disassemble. The job may look a little (or a lot) daunting with all those wires exposed, but it really isn't nearly as difficult as it looks and is often a much better choice than replacing an entire light fixture.
There will be three basic steps to changing out a ballast; removing the old ballast, choosing a new ballast, and wiring the new ballast into the fixture.
The steps are probably best when carried out in that order because it will be handy to have the old ballast in hand when buying a new one, so let's start with the first task listed.
Removing The Old Ballast
Fluorescent fixtures are designed and built with the idea that the ballast can be changed out one day without removing the whole fixture from the ceiling, but that doesn't mean that it is obvious or even easy for some fixtures.
In general fixtures that use four foot fluorescent lamps will have a channel running the length of the fixture and the ballast is located behind that raised portion of the fixture. While it is sometimes possible to remove a ballast with the lamps in place it is seldom worth the effort, so begin by removing all the lamps.
The cheap, "garage" or "shop" lights will have a cover behind the lamps that usually has one fastener on one end of it; twist the fastener ninety degrees and pull lightly to remove the cover. With the fastener removed from the fixture slide the cover toward that end; the other end has small clips that simply slide into place to hold the cover.
Be careful of the edges of that cover as it is thin sheet metal and can make a nasty cut if you slide your hand or fingers down the edge! I have been cut clear to bone simply by brushing lightly down the sharp edge of the cover with my hand - don't let it happen to you.
Better quality fixtures will typically need to have a plastic lens removed, then the lamps followed by a sheet metal cover over the ballast.
This cover is removed by squeezing the sides together, pulling the edges of the cover from under small clips on the fixture. Occasionally the cover may be screwed in place, but that is rather uncommon.
The cover will then need to be worked out from the lamp holders on each end, but this is merely a matter of holding and turning it just right to clear them. The lamp holders do not normally need to be removed.
Some lights may need to have the entire reflective shield removed after taking the lamps out, and there will be a variety of possible methods to do this. The shield may be screwed in place, it may have some of the small twist clamps or it might even need to have other pieces removed first. There is no standard method of "hiding" the ballast and it may require some head scratching to find it, but it is always possible.
The fixture shown below is an expensive one often used in large stores that has been hung in a shop to provide lots of light, but it is still very similar to cheaper home fixtures in what must be done to change a ballast.
Some homes will have a two foot square fixture and these can require a little more effort as the ballast may be hidden in one end, but it is still a matter of figuring out where it is and removing cover plates to find it. They are intended to be replaceable and can be reached without undue effort.
With the cover removed and the ballast exposed it is time to remove the old ballast. Make sure the power is off! I cannot recommend enough the use of a voltage tester here. I always carry a non-contact voltage tester on the job and check everything that even might be powered up. Getting a nasty shock while standing near the top of a ladder isn't much fun - don't let it happen to you.
The switch can be turned off, turning the light off, but if you choose to do this rather than turning the breaker off at the panel it is suggested that you tape the switch(es) off with some electrical tape. It is too common to have someone else walk into the room and automatically flip the switch on as they do, just as you have your hands around the wires they are turning on. Make it obvious that the switch should not be turned on.
However you choose to turn the power off, make sure it is off and will not be turned back on while you are working. Tape the switch off so it can't be turned on by accident or turn the breaker off and tape the panel door shut. You don't want to turn a breaker off and then have someone realize that the lights in another room are off, find the "tripped" breaker and turn it on.
Undo the wire nuts on the black and white wires, putting the wire nuts back onto the wire not connected to the ballast as a safety measure. Cut the rest of the wires a few inches from the ballast, using wire cutters.
With covers and lamps out of the way, the ballast is most normally removed by removing a small nut or screw on one end and sliding the ballast towards the screw and out from under the clips that hold the other end.
Safety First, Always!
Personal safety cannot be emphasized enough when working around electricity. The non contact voltage detector shown above is a perfect example of how to protect yourself. Make sure you work safely, please.
If you need one of these nifty tools, a link is given below to purchase one and the link shown here will take you to an article listing various models and giving instructions on how to use one.
Non Contact Voltage Detector from Amazon
Magnetic vs Electronic
Magnetic ballasts are generally rapid start and have two wires to each tombstone while electronic ballasts are usually instant start and usually have only one wire per lampholder. Matching wire colors, number of wires and number of lamps will give a ballast that be used as a direct replacement without re-wiring the tombstones. Electronic rapid start ballasts are available that will replace a magnetic ballast without re-wiring the lampholders.
Choosing A New Ballast
Older ballasts (most likely the one you are replacing) are generally the magnetic type, while newer ballasts are of the electronic variety and are more efficient. Ballasts can be either rapid or instant start, and are specific as to the number and type of lamps they operate. Magnetic ballasts are typically of the rapid start type but can still operate 1,2,3 or 4 lamps and must have the proper number of lamps. Electronic ballasts can operate a fewer number of lamps than they are designed for, but it is still a good idea to purchase the right ballast.
A ballast designed for T12 (the larger diameter 4' ones) will not operate a T8 (smaller diameter but more efficient) lamp even though the T8 lamp is still 4' long. The wattage is different and the ballast must be matched to the proper wattage. Take note of the wattage stamped on the lamp and purchase the appropriate ballast according to what is already in the fixture, the wattage of the lamp and how many lamps that the ballast is operating. Some fixtures have two ballasts in them, so make sure you know how many lamps the replacement ballast must operate.
The older magnetic ballast may be replaced by a newer, more efficient electronic ballast but it will likely require re-wiring the tombstones (lamp holders). Should you choose to do this (recommended) the tombstones will have to be removed as well, the wires removed from them, and new wires put in according to the wiring diagram on the new ballast. The wiring methods may be different for magnetic and electronic ballasts and this must be corrected if the type of ballast is to be changed.
Installing The New Ballast
You will need a handful of small wire nuts (one for each wire) and a pair of wire strippers.
Attach the ballast in the same manner as the old one. In very rare cases the physical size will be different; if this is the case it can be simply screwed to the top of the fixture with self tapping sheet metal screws. Just make sure it is within the footprint of the cover as necessary.
Splice the black and white wires to the matching colors, using the wire nuts that were on them originally.
If the ballast is of the same type as the one removed, match color to color on the wires and splice them together. A red wire, for instance, from the ballast will go to a red wire from a lamp holder and although there may be two from each it won't matter which one goes where. Just don't splice the two red wires from the ballast together thinking one is from a lamp - I've seen this done from the factory and it does not work well!
If a different type of ballast is being used, follow the wiring diagram on the ballast and change the wiring to the tombstone as necessary.
With the wires all attached, replace the ballast cover, lamps and any lens that was removed. Turn the light on to check it.
More by this Author
How to add a new outlet and wire it into an existing circuit. Complete instructions, including tips on running the wire and actually wiring the outlets.
Instructions on how to bend both 3 point saddles and 4 point saddles in EMT electrical conduit.
Math formulas and multipliers to help you bend electrical conduit. Learn how to bend conduit to any configuration desired, not merely the common bends on a conduit bender.